Per Florida Building Code
2322.214.171.124.1 Manufacturers of prefabricated wood truss assemblies shall obtain a valid certificate of competency from the authority having jurisdiction.
23126.96.36.199.2 Each truss shall bear the fabricators stamp on a web member and 75 percent shall be placed so as to be clearly visible after erection and before placement of ceiling.
23188.8.131.52.3 Multiple member girder trusses shall be predrilled at the truss plant for connection bolts only. Hanger bolt holes shall be drilled on-site on location indicated on approved drawings.
23184.108.40.206.4 Each manufacturer or fabricator shall retain the services of applicable organizations among those listed below for monthly inspections of the lumber grade used in fabrication. Following each inspection, a report shall be submitted by the inspection agency to the authority having jurisdiction. All inspection agencies providing any type of inspection services shall be approved by the authority having jurisdiction.
|For Pine:||Southern Pine Inspection Bureau or Timber Products grading agencies with appropriate jurisdiction.|
|For Douglas Fir, Hem-Fir or Fir-Larch:||Western Wood Products Association or West Coast Lumber Inspection Bureau. Timber Products Inspection Inc. or other grading agencies with appropriate jurisdiction.|
23220.127.116.11.5 In addition, the fabricator shall employ an approved testing laboratory to conduct inspections of fabrication compliance. Such inspections shall be made unannounced and at random at least once a month. Following each inspection, a report on approved forms shall be submitted by the laboratory to the authority having jurisdiction and such reports shall bear the date, signature and seal of the supervising Florida-registered architect or professional engineer.
2318.104.22.168.6 When there is evidence of noncompliance with the provisions for fabrication set forth in this paragraph or with the approved plans, the authority having jurisdiction may require the inspection laboratory to make additional job-site or plant inspections.
2322.214.171.124.7 The authority having jurisdiction may require load testing on noncomplying wood trusses. The test results shall be reported to the authority having jurisdiction.
23126.96.36.199.8 Failure of units tested or receipt of inspection reports indicating fabrication not in accordance with approved truss design drawings, or failure to submit required inspection and/or test reports, shall be cause for suspension or revocation of the certificate of competency of the manufacturer or fabricator.